On May 6, Bruce A staff discovered a small amount of water from the heat transport system (approximately 200 millilitres, which is less than a pop can) on the floor of Unit 3. Tritium was detected in the area andREAD MORE
Bruce Power continues to monitor the release of mineral oil, which occurred Thursday night when a transformer failed outside Unit 8. The unit was offline for planned maintenance. A mineral oil sheen was observed late this morning in the station’sREAD MORE
On Dec. 6, a failure of a transformer outside the Unit 8 building at the Bruce B generating station, resulted in a release of mineral oil. The unit was offline for planned maintenance. There is a collection system designed andREAD MORE
An employee is back to work today after an electrical contact event on Monday, Oct. 15. The employee was conducting welding work on a boiler system during Unit 8 outage activities when they received an electrical contact. The employee leftREAD MORE
Unit 3 was returned to service after a seven-day forced outage.
Unit 3 was removed from service for a forced outage.
Unit 4 was returned to service after a 105-day planned outage.
A Bruce Power Boiler Safety Relief Valve in Unit 4 was opened in the early afternoon on June 15. Steam from the valve on the roof of the Bruce A generating station produced a sound that might have carried beyondREAD MORE
Unit 8 was safely returned to service after a brief forced outage.
Unit 8 was safely removed from service for a forced outage.